|Jacket Pipe||Medium pipe||Bending radius||Water content||Heat capacity||“U” Value|
|Art. No.||dout (mm)||dout/s/din||DN (din)||[m](1)||[l/m](2)||avg [kW](3)||[W/(mK)](4)|
(1) The indicated minimum Bending Radius can be applied permanently without affecting the system’s quality or performance
(2) The Water Content is expressed in liters per meter length of pre-insulated pipe, including flow + return volume
(3) Average Heat Capacity in kW for the carrier pipe (at Twater of 80°C with a ΔT of 20°C)
(4) The U-value enables easy heat loss calculation, as a function of the driving temperature difference (calculation method: see page 46)
The installation of adequately anchored Fix Points at the system’s extremities (typical at wall penetrations) is mandatory. This to secure the connected plumbing against the potential impact of the system’s dilatation forces (thermal expansion/retraction). Failing to do so involves a genuine damage risk, and automatically voids the system warranty.
To prevent ingress of (ground)water, the EN 15632-3 standard prescribes the usage of Shrink End Caps to seal the non-bonded system layers at underground connections. Failing to do so involves a genuine damage risk, and automatically voids the system warranty.